The module provides analog signals output and data receipt via RS-485 interface.
The module is intended for receipt of digital coded signals via RS-485 interface and their transformation into output digital and analog DC signals (solid state relay, current signals from 0 to 20 mA).
The module is intended for operation as part of design-specific distributed fire and security alarm systems and shall be mounted on structural elements (cabinet, floor panel) of KTS-2000, KTS SA.
The module can be restored and repaired, it is intended for day-and-night continuous operation.
|Number of digital output signals||8|
|Number of analogue output signals||4|
|Resolution of setting voltage and current, bit||16|
|Number of groups||4|
|Number of signals in a group||2 discrete and 1 analog signal|
|Output digital signals||Solid state relay is generated|
|Switched current (AC/DC), mА, max.||40|
|Maximum switched voltage at active load, V, max.||36|
|Output analogue signal, mА||0..20|
|Current signals load resistance, Ohm, max.||500|
|Conventional error limit throughout temperature range, %||0,25|
|Supply voltage range, V||18..36|
|Consumed power, W, max.||5|
|Overall dimensions, mm, max.||150x80x40|
|Weight, kg, max.||0,4|